Operation principle of micro filter equipment
The equipment is continuous filtration. When the water enters the drum, the automatic control system will start the driving system and drive the cylinder to rotate, and start the backwash pump at the same time. The drum starts to rotate slowly, and the backwash pump draws the filtered water and backwash the filter screen. The particulate matter washed is collected by the backwash water collecting tank inside the equipment and discharged through the drain pipe. At the same time, the filter runs normally. When no water passes through the equipment, the equipment will stop automatically.
Equipment main body
The rotary filter housing is made of 304L stainless steel, including central intake pipe, rotary drum, linkage gear, rotating bearing, seal and so on. The upper end of the central rotary drum is provided with a collecting drain tank. All the main parts are made of 304L stainless steel.
The PII precision filtration equipment is combined with automatic control and manual control in the operation of the filter system, and the control system is made by the standards of the International Electrical Manufacturing Association. Monitor and control equipment operation according to process design requirements.
The control cabinet is made of cold rolled steel sheet and the surface is treated by polyester powder spraying. The protection level is IP65.
Control box set - stop button, automatic - manual switch, emergency stop button, single device open - stop - fault indication, all control and protection circuit separate, button and indicator light match.
The system is controlled by PLC.